I have 2 chillers in my chilled water plant loop. These two chillers are identical and they are connected to same condenser loop. Chiller 1 has the first priority in the plant equipment operation and it is work without problems. the chillers 2 with second priority and loop load distribution of sequential works really strange. the chiller 2 has design loop exit temperature of 6 C and Setpoint manager with scheduled always 6 C on supply water. However, the results show supply water temperature varies between 10 to 20 C. I dont understand why chiller 2 does not follow the setpoint manager for supply water temperature.
I appreciate any help or idea to make it work properly
Help and discussion on using the Detailed HVAC option
Moderator: DesignBuilder Support
1 post • Page 1 of 1
Who is online
Users browsing this forum: No registered users and 2 guests